This smoke alarm guide helps you understand a smoke alarm system. You could use the guide to DIY your smoke alarms. Alternatively, to educate yourself before you engage an installation contractor. The online smoke alarm calculator gets you off to a flying start. It also helps you check and record your design. Template, smoke alarm floor plans provide examples of installations in a typical dwelling.
Smoke alarm calculator
Use the free, online smoke alarm calculator below to determine your needs.
Mains powered, wire interconnected smoke alarms are required for all new properties.
Firstly, do you have mains powered alarms now? To clarify, mains powered alarms incorporate a green LED.
If no, a non-electrician install is simplest for you.
On the other hand, if yes, you could leave your existing mains powered (green LED) alarms in place and still perform a non-electrician install. Alternatively, you may prefer to use mains powered alarms and hence pursue an electrician install.
In short, just install 10Yr lithium battery powered alarms with wireless interconnection. As a result, non-electricians can install these detectors. So for this arrangement, download the sample smoke alarm floor plans below.
If you are adding mains powered smoke alarms you may need access to the roof space to run additional wiring.
So in the case of a low set property with roof space wiring access, download the sample floor plan below.
But wiring access in the roof space for the new mains powered alarms may not be convenient or even possible. In addition, it is unlikely that you will have wiring access to the ceiling space between floors in a high set dwelling also.
So this is an occasion when you will have a mix of smoke alarm types. In other words, a hybrid system including both mains and battery powered alarms that interconnect both wired and wirelessly. So for this arrangement, download the sample smoke alarm floor plans below.
In general, smoke alarms are required along escape routes from each level. In addition, they are either strongly recommended or required in each bedroom. Why? Because, charging phones in bedrooms with the door closed adds fire risk and alarm awareness risk to sleeping occupants.
Smoke alarm floor plans – more details?
Once you have used the smoke alarm calculator and digested the relevant floor plan examples you may want to work out the exact SmokeSight models and quantities for your home. Although most of the time, the information in the sample layouts will allow you to determine your needs. But, if you have a larger installation or you need a hybrid system, you may want to consult the Smoke Alarm Designer.